All things related to HVAC
Room automation station BACnet / IP and DALI, for up to 8 rooms / 16 room segments
As of October 2016:
Device doesn't respect the requested segmented window size.
It asks for 4, but wait for an ACK after 2 :
Consequences : communication will timeout, or take much longer if the client device has an automatic fallback.